International Building Code Section 3008.8 is hereby amended to read as follows:
3008.8 Electrical power. The following features serving each occupant evacuation elevator shall be supplied by both normal power and emergency power in accordance with Section 2702 and Table 2702:
1. Elevator equipment.
2. Ventilation and cooling equipment for elevator machine rooms, control rooms, machine spaces and control spaces.
3. Elevator car lighting.
3008.8.1 Determination of emergency power load. Emergency power loads shall be based on the determination of the number of occupant evacuation elevators in Section 3008.1.1.
(Ord. 6531 § 5, 2020.)